In this article you will read a review of a SHT2000 combined temperature controller with a humidity controller that can control both humidity and temperature at the same time ,can see and download manual ,wiring conections and more useful info.
Here are the pros and cons of SHT2000 temperature humidity controller:
Here is pros
- Red/Blue Color display
- If you need upgrade controller has same dimensions as temperature controller MH1210W or MH13001
- Two independent relays (one for temperature and one for humidity)
- Good price – the price is cheaper than you would buy two devices separately
- Stable and accurate temperature and humidity measurement
Here is cons
- Possibly setting the target values for the first time will be difficult
- Range is smaller (-20°C +60°C) but for a hatchery or a drying room is stil OK.
- Temperature reacts slower than humidity
Review conclusion for SHT2000 controller:
First, I start with negative features The thermostat responds more slowly than the 1210W model or other NTC 10K probe.this is caused by the SHT21 Probe temperature sensor is inside the plastic sensor and it takes some time until the temperature changes. Control range is smaler comparison with 1210w temperature controler. Setup is also difirent no have menus – HC ,P7,HS,LS, temperature and humidity settings are the same as XY-WTH1 .
Positive qualities for SHT 2000 are color-coded temperature humidity on display,Precise Moisture Measurement after stabilization, the temperature is accurate.
Manual SHT2000 temperature controller
Complete video manual with setings for humidifing/dehumidifing – heating/cooling and Calibration:
Setting method: Start value > stop value (the program automatically determines the working mode is cooling/dehumidifying mode)
Heating/cooling mode setting
Setting mode: setting (starting temperature): Press and hold the ▲ button to start the temperature flashing. Use ▲▼ key to set the starting temperature value.
Setting (stop temperature): Press and hold the ▼ button to stop the temperature flashing. Use ▲▼ to set the stop temperature value.
The first step: heating mode, starting temperature <stop temperature
Step 2: Press and hold the ▲ button to start the temperature flashing. Use ▲▼ to set the starting temperature to 50 °C.
Step 3: Press and hold the ▼ button to stop the temperature flashing. Set the stop temperature to 65 °C with ▲▼ keys, and the setting is completed!
The first step: cooling mode, starting temperature > stop temperature
Step 2: Press and hold the ▲ button to start the temperature flashing. Use ▲▼ to set the starting temperature to 30 °C.
The third step: long press the ▼ button to stop the temperature flashing, set the stop temperature to 26 °C by ▲▼, the setting is completed!
Setting (start humidity): Press and hold △ key to start the humidity value flashing. Set the humidity value by △ ▽ key. Set [Stop Humidity]: Press and hold △ key to stop the humidity value flashing, and set the humidity to stop by △ ▽ key value.
Step 1: Press and hold the △ button for 3 seconds to start the humidity value flashing, and set the starting humidity value to 50% RH.
Step 2: Press and hold the ▽ button for 3 seconds to stop the humidity value flashing. Set the value to 80% RH. After the setting is completed, the button will be operated for 5 seconds without returning to the normal display state.
Step 1: Press and hold the △ button for 3 seconds to start the humidity value flashing, and set the starting humidity value to 40% RH.
Step 2: Press and hold the ▽ button for 3 seconds to stop the humidity value flashing, set the value to 70% RH, the setting is completed, the button does not operate for 5 seconds, and automatically returns to the normal display state.
- Supply power : AC 110-230V
- Relay control output: 10A (1xtemperature 1x humidity)
- Humidity control range: 0-100%
- Temperature control range: -20°C +60°C
- Acurracy: +-0.3°C and +-3%
1x AC 110~230V 10A SHT2000 Temperature and Humidity Controller
1x Controller Meter SHT21 Probe